Code of Maryland Regulations
Title 09 - MARYLAND DEPARTMENT OF LABOR
Subtitle 12 - DIVISION OF LABOR AND INDUSTRY
Chapter 09.12.01 - Board of Boiler Rules
09.12.01.38 - Kitchen Equipment Boilers
09.12.01.38. Kitchen Equipment Boilers
A. Kitchen equipment boilers are exempt from the requirements of CSD-1, except that they shall have:
(1) An emergency shut-off switch located outside of the main point of access and egress to the kitchen, unless the installer can establish that this location would allow access by the general public that could be detrimental to the operation of the boiler; and
(2) A lockable service disconnect.
B. Control and safety devices for kitchen equipment boilers shall comply with:
(1) The code under which they were constructed and stamped; and
(2) The recommendations and requirements in the manufacturer's installation manual.
C. If a conflict between § B(1) and (2) of this regulation occurs, the code under which they were constructed and stamped shall be followed.(Regulation .38 adopted effective December 12, 2002 (29:24 Md. R. 1919))